We've just finished installing new generators and now the contractor has informed be that our new soot filters won't work because we're not getting enough load to get the temperatures high enough! You would think that said contractor would have been able to calculate all of this before ripping out the old gear! And, he was the guy who sold and installed the previous units too Anyhow, does anyone have any suggestions for a way to add load (appr. 10-15Kva), or for manufacturers of a small load bank? The pricing from the contractor is appr. $20K before installation.